Environmental guidance for your business in Northern Ireland & Scotland
Fume hoods or fume cupboards are used to prevent people working in laboratories being exposed to harmful or unpleasant gases and dust particles. Fixed fume hoods are usually connected to extraction fans which vent to the outside air. Modern equipment uses filters to prevent the release of harmful material to the environment.
Research activities are exempt from the permitting and reporting requirements of the pollution prevention and control (PPC) regime. Emissions from fume cupboards are not likely to contain large amounts of chemicals.
If you use organic solvents you must check that the total quantity of solvents used across your site does not exceed certain thresholds. There are thresholds set for each activity. See our guidance on solvent emissions for further information.
Emissions from the venting of fume hoods are likely to involve small quantities of gases, fumes or dust. You must prevent emissions of noxious or offensive substances. You should render these substances harmless or inoffensive before you emit them.
If your emissions cause annoyance to the surrounding community you may have to deal with them as a statutory nuisance.
Fume cupboards are classed as local exhaust ventilation (LEV) equipment and you must ensure that their design and fitting complies with British Standards. Depending on the age of your equipment, it should be built and fitted in compliance with BS 7258:1994 or BS EN 14175:2003. You must examine the equipment at least every 14 months. In practice, this is normally taken to mean annually. You must keep records for five years.
You must make sure that that the air being drawn into the fume cupboard has an average velocity of 5 m/s (metres per second). You must make sure that the minimum velocity at any point is 4m/s or greater.
If you use a fume cupboard for work involving radioactive substances you must fit it with a filter and label it as a Filtered Fume Cupboard.
If you use a fume cupboard for work involving reactive materials, such as hydrofluoric acid, which can damage pipework and the cupboard itself, then you should fit it with cascading water over the airflow outlet. You should label it as a Scrubbed Fume Cupboard.
You should treat used filters from fume cupboards as hazardous/special waste. You can identify contaminants from the Material Safety Data Sheet (MSDS) which is supplied with the chemicals you use.
You can find guidance on the steps you must take to comply with the Control of Substances Hazardous to Health Regulations (COSHH) from the Health and Safety Executive (HSE) or the Health and Safety Executive Northern Ireland (HSENI). These regulations have been amended to include work with biological organisms.
If you supply a potentially hazardous chemical, you may have to provide a safety data sheet (SDS). The SDS tells the user how to handle, store and dispose of hazardous chemicals.
For guidance about when to provide an SDS and what it should include, see the Health and Safety Executive (HSE) leaflet.
If you don't receive an SDS with a chemical, you can contact the supplier and ask for one. Suppliers who do not provide adequate instructions for using their products safely may be breaking the law.
BREXIT 'No Deal' Guidance, With BREXIT approaching and no sign of a deal there is some uncertainty surrounding what could happen to regulations and legislation.
Leftovers are ‘Good to Go’ this Festive Season, Our green ‘Good to Go’ scheme lets your customers know that their leftovers can be boxed up and sent home with them to be eaten later by the Christmas tree.
View our latest videos & subscribe to our channel.
Free monthly email newsletter with environmental updates for Northern Ireland and Scotland