Environmental guidance for your business in Northern Ireland & Scotland
Each separate piece of equipment will have its own equipment charge. It used to be the number of kilograms of gas in the system that was important for deciding the actions required for servicing and maintenance of a refrigeration or air conditioning system.
This has changed and it is now a measure of the effect the F-gases in the system could have on the atmosphere that is important. This is calculated by working out the quantity of CO2 that would have to be released to have the same warming effect on the atmosphere as the contents of the system.
This is known as the CO2 equivalent of the F-gas.
The CO2 equivalent of the equipment charge is calculated using:
Different F-gases have different global warming potential. This relates to its ability to absorb energy and add to the warming of the atmosphere. Two pieces of refrigeration equipment that have a similar capacity for refrigerant can contain different F-gases. If released, the impact on the atmosphere could be significantly different
The charge is calculated by multiplying the number of kilograms of F-gas by the global warming potential of the specific gas in the system.
Global warming potential of greenhouse gases, including typical F-gases. The F-gases are shaded.
|GAS||GWP (100 years)|
|R-404A (HFC blend)||3,922|
|R-410A (HFC blend)||2,088|
1kg of HFC-134a is equal to 1.43 tonnes of CO2
1kg of R-404A is equal to 3.92 tonnes of CO2
1kg of PFC-14 is equal to 7.39 tonnes of CO2
5 tonnes of CO2 is equal to:
How micro-brewers and distillers can reduce their environmental impact, A blog exploring the environmental obligations and responsibilities of micro-brewers and distillers, with advice on things they should and shouldn't be doing.
BREXIT 'No Deal' Guidance, With BREXIT approaching and no sign of a deal there is some uncertainty surrounding what could happen to regulations and legislation.
View our latest videos & subscribe to our channel.